Wiring and Commissioning Service
Offered as part of our pump station maintenance services, wiring and commissioning is a great way to make sure your new pumping station is up-and-running correctly.
Having arrived on-site, our trained engineer will:
- Notify the site agent of their arrival
- Inspect the site to ensure installation can be carried out
- Position vehicles so that equipment and tools can be easily off-loaded, without causing any obstruction
- Pull pump cables through the duct to the control panel location, using draw wire that was installed by the client prior to our arrival
- Gland off pump cables into the bottom of the control panel and terminate them internally in accordance with the wiring diagram
- Check pumps at ground level for rotation, by witnessing the direction of the impeller
- Suspend level control equipment and pull cables through duct to control panel (again using draw wire installed by the client prior to arrival)
- Gland off level control cables into the bottom of the control panel and terminate them internally in accordance with the wiring diagram
- Set the level control to the correct position
- Check pump overloads and set them appropriately to the full load current
- Test pumps, level control and control panel function in all modes
The main goal is to test all connections and ensure the station is working as it should. Once satisfied with its performance, we will issue a wiring and commissioning certificate for your records.
Before you get in touch to book a wiring and commissioning visit, please fill out the checklist below. This helps us to calculate an accurate quote (price above is a guide only) and confirms if your site is ready for our visit. If you would like to find out more about wiring and commissioning, or any of our other sewage pump station maintenance services, please feel free to get in touch – call us today on 0844 414 5800.
ADDRESS OF SITE
( Minimum of 9 days’ notice if not
To confirm that the site is ready prior to our attendance on site, please tick the circles that apply to your site. (If you have any problems in filling out this sheet please contact the office)
When sheet is complete please email to email@example.com
Commissioning cannot be carried out unless all circles are checked (please use a cross rather than a tick to indicate if materials are being brought to site by commissioning engineer).
o Rising Main (discharge pipe work) and gravity lines are connected to the tank.
o Gravity drainage lines have been flushed through to remove any building debris.
o Sump is clear /clean of debris and empty (not full of water or anything else)
o Cable ducts with draw wires are in place between the control panel location and the pump chamber.
o Control panel mounted prior to attendance with live, isolated electrical supply connected.
[ For Dual 240v Control Panels powered by a 32amp Type C Circuit Breaker Spur ]
[ For Dual 400v Control Panels powered by a 16amp Type C Circuit Breaker Spur ]
o Control Kiosk is mounted on a suitable plinth and secured down (if applicable)
o Check distance from the control panel to the bottom of the sump VIA THE CABLE DUCT (………M long) not a direct run. NOTE… Pumps and control floats have a standard 10m cable. Please add an extra 1.5 m for wiring etc.
o Extra cable, junction boxes and glands are the responsibility of the site. These can be supplied but at an extra cost. Please discuss prior to visit
o Normal earthling is acceptable.
o A water supply is available to fill the pump chamber so that the pumps can be tested.
o Upper guide brackets, guiderail, pipework and valves are fixed into the pump chamber.
o Finished access opening size is correct to the chamber size. This is to ensure the pumps can be passed through and installed correctly.
o Finished concrete cover slab openings should not be reduced in size otherwise the pumps may not fit.
o Please check that these items are on site:
o Pumps c/w guide claws and chains fitted
o Float switches.
o Twin pump stations 2no pumps and four floats
o Single pump station 1no pump and 3no floats.
o Please tell use of any Special parking arrangements need to visit site
This form has to be completed and returned before any commissioning works are carried out.
When this commissioning form has been signed and returned and the commissioning cannot be carried out, there will be an extra charge. The charge will be the full commissioning rate made payable prior to re-attending site.
If you are unsure that they site is ready for us to carry out the commissioning then please do not hesitate to contact the office on 0844 414 5800.
Any other comments regarding the commissioning that we should be made aware of:
Write a review and let shoppers know what you think of this product.
I just thought I would drop you a quick line to thank you for your supply & commissioning on my last project at the Olympic Park, I found your service immpecable; Delivery was without a hitch, equipment & drawings "all in the box" and backup on the end of the phone. Commissioning on the day agreed no fuss, with your engineers more than happy to help & advise in all aspects of the task. I just wish we were able to engage other contractors like yourself who "do what it says on the tin!"
Once again thanks for your help.